How many second we need to setting for changeover timer from STAR to DELTA sequence for Star Delta Starter?This question is very popular among electrician around the world when handling the Star Delta Starter for their application.
From my experience,honestly,it quite difficult to get the accurate times for star delta changeover.But we can get the approximate times with several monitoring technique and measuring equipment to decide the best setting for change over timer of Star Delta Starter.From this post,i would like to share some information and basic technique how to get the approximate times for Star Delta Starter change over timer.I hope from this post,it’s can give some ideas or clear view how to setting the times for Star Delta Starter change over timer.
How to get a time for change over of Star Delta Starter?
The important point that we should know about Star Delta Starter is when in STAR sequence it must running with 80% of full load speed for motor before change over to DELTA sequence.
From this point we can use it to get the approximate time for change over timer.Basically we can use the two measuring method following :-
1) Clamp on meter / ampere meter
This method we can measure the ampere during STAR sequence.It’s can start from 0 (zero) until peak value of ampere and it will in flat reading because the voltage applied for star delta starter to the individual motor winding is therefore reduced by a factor of 1√3 = 0.58 this connection amounts to approximately 30% of the delta values.
Prepare the stop watch to measure the time from 0 (zero) ampere until peak value during STAR sequence.After that use the time that we measure to setting change over for the Star Delta Starter timer.We need minimum two person to perform this measuring and start stop the starter.
2) RPM meter
We can measure the speed of motor when space is available or the pulley or shaft not covered such as air-compressor.From the basic point for Star Delta Starter is it must running 80% of speed of motor,we can measure the speed of motor (RPM) during STAR sequence.
Set the stop watch and measure the time from starting (0 rpm ) until it reach 80% of motor speed.example if full motor speed is 1400 rpm,so for 80% full speed is around 1,120 rpm.So stop the watch and take the time reading.
That is the time for change over from STAR to DELTA sequence.Setting your timer with the time that we record and test run for full sequence and take a look if it have any abnormal phenomena.
Conclusion about timer setting for Star Delta Starter
These two method that i’d explained above is a basic measurement technique that we can use to determine the approximate time for change over of star delta starter.
It’s not 100% accurate but at lease we can get the approximate time for change over timer of Star Delta Starter.Normally the base line for timer setting is around 10 until 20 second.
We can use the try and error method to get the best time for change over from STAR to DELTA.Any suggestion,ideas or comment,please share it on my comment box.We can discuss this issue from different perspective.